J – 8 to 24 Zone Expandable Control panel. FireClass J Details Manuals / Documents Approvals / Declarations of Conformity. MAIN FEATURES. BENTEL SECURITYsrl shall not assume the responsibility for damage arising from improper application or use. Manual Extinguishment Input. + Add to cart. Specification; Documents. Manufacturer. BENTEL. Part number. J Number of zones. 8. Zone expansion up to. Supply voltage. V AC.
|Published (Last):||23 September 2014|
|PDF File Size:||1.59 Mb|
|ePub File Size:||1.72 Mb|
|Price:||Free* [*Free Regsitration Required]|
Comments to this Manuals Your Name.
Manual Automatic valve Hentel. Installing Repeaters Installing Repeaters Installing the Control panel Work carefully through the following steps see the Fi – The Display Module if used must be installed be- gures on pages 10, 12 benfel Button n Pre-extinguishment Phase n Manual Extinguishment If the programmed extinguishment conditions occur The Extinguishment Module can be activated from ma – programmed by your Installerthe Extinguishment nual call-points ask your Installer for details.
Bentel Security | Products > Fire Products > Repeater Panel – JREP
Install the Extinguishment Module, as follows. ZONE 1 Warehouse 4. To download a specific page: Lastmanuals offers a socially driven service of sharing, storing and searching manuals related to use of hardware and software: Page 10 Logic Extinguish. Silence status will be signalled by: Insert the reverse locking supports 93 into their respective locations 94 as per Fig. In any way can’t Lastmanuals be held responsible if the document you are looking for is not available, incomplete, in a different language than yours, or if the model or language do not match the description.
Telecom Mains Mains Disab. Connecting A Power Supply 60 and jumper connectors.
The J and J Control panels provides the follo – wing features: Output Voltage of the Switching Power Supply to the indicated value. ON glowing indicates that the program – med Investigation time is running. Disable Extinguishment Input [IE] terminals. Expander Module Install Expander Modules as follows. Designated trademarks and brands are the property of their respective owners.
Display Door screws Unless otherwise stated, the numbers in boldface in this Keyswitch Access Level 2.
Bentel J424 Installation Manual
Display Door screws Unless otherwise stated, the numbers in boldface in this Keyswitch Access Level 2 Page 15 Flat cable accessory item: Expander Modules Accessing the Programming session Enrolling: The control panel has supervised and silenceable alarm outputs for the control of the selfpowered sirens, piezoelectric sirens, fire bells, flashers, telephone diallers, etc. The device concerned has been restored Table 2 Event Descriptions Continues Flat cable accessory item: Installing Repeaters Installing the Control panel Work carefully through the following steps see the Fi – The Display Module if used must be installed be- gures on pages 10, 12 and Enter text from picture: Connecting Call-points Figure 15 Wiring diagram of 3 detectors with Normally-Open Outputs and a Call point with zero ohm contact resistan – ce: PS Input of Extinguishment Mod.
PS Input of Extinguish. Once the operating parameters have been set up, they To Download several pages: Expanders Modules must be installed befo- re mounting the Control panel to the wall. This easy-to-use control panel is protected by a lockable frontplate which allows operational access to authorized personnel only.
Page 12 Figure 2 Maximum configuration of the J Control panel J Installation Manual English v2. J Declaration of Conformity English.
Related Manuals for Bentel J No related manuals. It has 8 zones main board and supports two JEXP8 expander modules, for a total of 24 zones and devices maximum 32 in each zone. Up to 1 A can circulate on the PR Output. Remove the screws 4 and open the Con- trol panel. EN54 and EN approved with JEXT extinguishment module 8 controlled, balanced, bypassable input zones expandable to 24 by means of two 8 zone expanders Up to 32 devices can be connected to each zone but no more than in total: If this document matches the user guide, instructions manual or user manual, feature sets, schematics manuap are looking for, download it now.
Page of 64 Go.
This manual also for: By pressing ‘print’ button you will print only current manuap. Installation of this Control panel must be carried out strictly in accordance with the instructions described in this manual, and in compliance with the local laws and bylaws in force The J and J Control panels comply with the essential requirements of standards EN; EN Don’t have an account?
Type Product name to find it. The J control panel is also available with a backlit display, which shows all the information regarding the control panel status.
User manual BENTEL SECURITY J424 INSTALLATION